http://oceanadesigns.net/images/granite/persa-avorio/persa-avorio.jpg Use Of AFM For Chromium 6 Removal –
go Chromium is occasionally found in ground water in trace amount from 1 to 10 ug/l however the occurrence of chromium is usually associated with pollution from industries such a leather tanning, wood preservation and textiles. Polluted ground water may have much higher concentrations.
Hexavalent Chromium is very difficult to remove down to low concentrations, however AFM® can adsorb Cr6+ directly from the water. If the concentration is low then it may be possible to just filter the water through a deep AFM® filter bed >1200mm at a slow flowrate , 5m/hr. This may be all of the treatment required.
AFM® has a low capacity for chromium, so in order to improve performance water pretreatment may be required The Cr6+ is reduced to Cr3+ by using a reducing agent such as ferrous sulphate or calcium polysulphide. The reaction takes time, so a buffer tank of more than 30 minutes is required.
After the 30 minute contact tank, the water overflows to a second contact tank which is aerated, this oxidises any remaining ferrous to ferric which co-precipitates and flocculates the Cr3+ to form a solid particle than can be more easily removed by AFM®. The bed may take few week to get conditioned to chromium.
- .The pH of the water to be treated should be above pH7.5
- Ferrous sulphate, and lime/calcium polysulpite may be injected into the water via a ZPM cavitating static mixer. Application rate approx. 20:1, 20 ferrous to 1 Chromium, and 5:1 for the calcium polysulphite
- After injection the water enters a sedimentation decantation reaction tank for at least 30 minutes.
- After decantation to water enters a second 30 minute retention tank for aeration. The aeration level is the same as water flow, if water flow is 50m3/hr air flow is 50m3/hr applied via Dryden Aqua air diffusers. The aeration is not sufficient to oxidise the Cr3+ back to Cr6+ but it is sufficient to oxidise the Fe2+ to Fe3+ which helps to co-precipitate the Cr3+
- The water is pumped out of the aeration tank to an AFM pressure filter.
Pretreatment of the water prior to filtration by AFM® is very important. AFM® will remove Cr6+ and Cr3+ by the following mechanisms:
- Direct adsorption of Cr6+ ion on to AFM®
- Direct adsorption of chromium Cr3+ : ferric particles onto the –ve charged surface of AFM
- Physical filtration of most particles down to 1 micron
- Back-washing with water will completely remove the Chromium
- Back-wash water sludge should be separated and disposed of responsibly
source site Other AFM Application Areas
AFM® reduces the biological risk from bacteria and parasites as well as the chemical risk from water and air just above the surface. The result is a safer pool for children, a healthier work place for staff in public pools and a greatly improved swimming experience for everyone. Read More…
SWRO – Sea water reverse osmosis has found a great importance today as a technology for the reclamation of brackish water or sea water and making it potable enough for human consumption or industrial applications. Read More…
UF, RO membranes & DM plant resins work best when they are new and clean. Fouling of the membranes by inorganic and organic contaminants as well as biofouling are some of the main issues effecting the performance and cost of running water treatment systems.Read More…
Arsenic is often found in borehole / tube wells and ground water at varying concentrations depending upon the geology of the ground. In India western states along with certain locations in the south have fairly high contamination of Arsenic in the ground water. IN certain cases Arsenic is also found in the waste water effluent of certain industries. Read More…
Iron and manganese are often found in borehole / tube wells and ground water at varying concentrations depending upon the geology of the ground. Read More…